Another Red Card, so many issues with this stove!
1) Found a rust hole in the twin wall flue system in the loft space
2) No safety barrier around the twin wall flue system in the loft space
3) Twin wall flue system has been fitted to close to the wooden structure in the loft space
4) No fire stop in between ceilings
5) No visual access to joints in the chimney breast
6) Halve was too small for the size of the stove fitted
7) No carbon monoxide alarm in the property